|| 120 VAC
||Designed to operate with all major low water cut-offs and pump controllers. Upon a low water signal from the boiler control, the VXTC delays (from 0 to 10 minutes) to allow condensate to return to the system. If make-up water is required following the delay period, the VXTC initiates a feed cycle. The VXTC can be set to feed to the level of the boiler control or to varying levels above. The heavy-duty water meter tracks all water fed into the system. The VXTC includes
water feeder, strainer, flow restrictor and water meter with 3/4″ NPT fittings.